According to Jerry Spetzman, Chisago Lakes Lake Improvement District’s Administrator, the highlights of today’s (May 16, 2019) inspection are as follows:
Lofton Weir. The water level elevation at the Lofton weir yesterday, May 15 was 899.06 (per Chisago County Surveyor). This elevation is a good representation of the water levels of Chisago/South Lindstrom/North Lindstrom Lakes. The Ordinary High Water (OHW) level of these lakes is 900.2. The lakes are approximately one foot below OHW. According to the Operation and Maintenance plan both the high and low weir control gates are to be open when the water level exceeds 899.2. The high weir was opened on April 19. At that time water levels were not high enough to flow over the weir. On May 9 the Low weir was opened and water is flowing through the weir into Green Lake. The weir will remain open until water levels are lowered to 898.7 at which time the weir will be closed.
Paradise Park Weir. This weir is a fixed cable concrete weir. The weir has a permanent outlet elevation of 899.2. Today the water level from Chisago Lake is below the crest of the weir. No water is flowing from Chisago Lake over the weir toward Wallmark Lake.
Lake Ellen Weir. The water level at the Lake Ellen weir today was 891.31. This is a good representation of the water levels of Green/Little Green/Ellen Lakes. The OHW of these lakes is 892.5. The weir is to be open during the open water season when water levels exceed 891.0. The weir was initially opened on April 10. Water is flowing through the weir into Swamp Lake. Unless downstream issues arise, it is anticipated the weir will remain open until fall.
North/South Center Lakes. Yesterday, May 15, the water level of South Center Lake was 899.06 (per Chisago County Surveyor). This elevation is a good representation of the water levels of North and South Center Lakes. The Ordinary High Water Level of these lakes is 900.2. The lakes are approximately one foot below OHW.
LID staff are taking weekly lake level readings on other lakes in the Chisago Lakes area. These readings will be made public once the DNR calibration process is complete.
The Chisago Lakes Channel & Weir system is being actively managed according to the guidelines established in the 2016 Channel & Weir – Operations & Maintenance Plan. A copy of the plan can be found at:
Since early April, Lake Improvement District staff along with the LID engineer have been conducting weekly inspections of the channel & weir system. Attached is a copy of the April 25, 2019 Spring Channel and Outlet Structure Inspection report which summarizes activities in April. Inspection reports from previous years can be found athttps://www.chisagocounty.us/321/Channel-Weir-Maintenance-Reports